Ceiling Fan Wiring Instructions by Wire Color
Wiring a ceiling fan is surprisingly simple. Often times it is no more complicated than the wiring of a light fixture. As with any electrical wiring, make sure all wire connections are made securely with the proper size wire nuts, that they are not loose and that no copper strands are showing. Most "house wiring" should be 14 or 12 gauge solid copper wire attached to a 15 or 20 amp 120vAC circuit respectively. Consult a professional if you encounter something varying from this and are not aware of how to safely handle it.
Most commonly ceiling fans will have 4 wires, or 3 wires plus a ground. Black, white, green, and an additional color (usually red, blue, or black/white striped). The black wire is the hot lead for the fan motor. The red/blue/striped wire is the hot lead for the optional light kit. The white wire is the neutral lead for both the fan motor and light kit. The green wire is ground for the entire assembly.
In all cases the neutral (white) wire from the fan assembly should be attached to the neutral (usually white) lead from the house wiring. Note that if you encounter a white wire with a marking piece of colored tape attached, this could be used to signifiy it is being used as something other than a neutral.
The ground (green) wire or wires from the fan assembly should be attached to the ground (usually bare, sometimes green) lead from the house wiring. Some older houses may not have a separate ground lead and use the metal conduit and electrical boxes as ground. In this case you would attach the ground wire from the fan to the electrical box (and/or mounting plate) with the appropriate screw or clip.
As for the two hot leads:
Example 1: Replacing a light fixture with a fan, and/or installing a fan where there is only one switch
The black wire from the fan would be connected to the hot lead (usually black, sometimes red) from the house wiring. If the fan has a light the red/blue/striped wire would ALSO be connected to the hot lead from the house. If not then this wire would be capped off, should you chose to connect it (and make easier the option of adding a light later) make sure it is capped off in the fan's switch housing. In this example both the fan and the light would be controlled by the previous light's wall switch.
NOTE: examine the wires inside the electrical box. Is there an additional wire, presumably a black or a red? There is possibly another hot wire, unswitched, that would allow the fan's light to be controlled by the wall switch and the fan to be controlled by it's pullchain. In most cases you would connect the black wire from the fan to the black wire(s) in the outlet box, and the red/blue/striped to the red wire from the house. HOWEVER this can vary due to your house's wiring, so do not make any attempts unless you are sufficiently comfortable working with electricity.
Example 2: Installing a fan to a box already wired for one, where there are two switches
Some newer homes come pre-wired for fan-light combinations, and offer two separate wall switches: one for the light, and one for the fan. In this case you would connect the black wire from the fan to hot (black) lead from the house wiring, and the red/blue/striped wire from the fan to the additional hot (red) lead from the housing wiring. This should allow you to switch the fan and light separately. Should you chose to install a fan without a light, cap off both red (blue etc) wires, or connect them and make sure the light lead is capped off in the fan's switch housing.
Example 3: Installing a fan where there is NO switch
Connect the black wire from the fan to the hot (black) lead from the house wiring. If the fan has a light, connect the red/blue/striped wire to the hot (black) lead from the house wiring as well. Both the fan and light are to be controlled from their appropriate pullchains.
Example 4: Installing a fan with a remote
Remote controlled ceiling fans only have one hot lead for both the light and fan, as they are controlled internally by the remote receiver. In the cases of Examples 1 and 3 above, the fan would be wired as stated ignoring all references to a red/blue/striped wire. As in example two, only one of the two wall switches would be needed. You would connect the hot lead from the fan to either of the hot leads from the house wiring, and cap off the other.
In any case where a fan motor is controlled independently from a wall switch (such as Example 2 above, or Example 1 where there is no light kit) the wall switch can be replaced by a fan speed control to allow more diverse operation of the fan from the floor level. If both the fan and light are wired to the same wall switch a speed control should not be used.
Subsequently, when a fan light is controlled independently by a wall switch (Example 2 above, or as covered in the additional note to Example 1) and incandescent bulbs are used, the wall switch could be replaced by a dimmer switch to allow more diverse control of the light. DO NOT under ANY cirumstances allow a fan motor to be controlled by a dimmer switch.
Lastly, optional kits are available to convert a conventional ceiling fan (with light) into a remote control fan. The wiring of said kits can vary by case, so consult the included manual. However in most cases, the fan is wired to the kit's remote receiver as would be wired in Example 2 above. The kit's receiver would be connected to the house wiring as in Example 4 above.
See, nothing's that complicated.
Ceiling Fan Wiring
Electrical Residential Wiring Book
How to install a Ceiling Fan with Chad Smith
Westinghouse Ceiling Fan Switch
Lutron Electronics Dual Slide-To-Off Fan and Light Control
Health Zenith Wireless Command Lighting Indoor Wall Switch
Ceiling Fan Wiring Instructions by Wire Color Frequently Asked Questions (Faqs)
- Harbor Breeze LKD52WW6C Ceiling Fan Stopped Working - Where can I find a Wiring Schematic?
We have a 52" Harbor Breeze ceiling fan that was installed in 2007 and the fan has quit working a couple yrs ago. Need schematic diagram for it to get it fixed. Model #LKD52WW6C. Is it possible to get this?
- How do I wire a dual switch ceiling fan to work with a remote control?
I unhooked my old fan and hooked up my new fan, but my remote does not work. I need help with the wire colors - I have red, white, black and green wires that are coming out of the ceiling. Also, I need to wire up my remote control. Help?
- Ceiling Fans Frequently Asked Questions